Dr. Murphy graduated from the University of California, Los Angeles David Geffen School of Medicine in 1970. He works in Reno, NV and specializes in Infectious Disease. Dr. Murphy is affiliated with Carson Tahoe Regional Medical Center, Renown Regional Medical Center and Saint Marys Reno Regional Medical Center.
Name / Title
Company / Classification
Phones & Addresses
Franklin Glen Murphy Real Estate Agents and Managers
600 N Pearl St, Dallas, TX 75201
Franklin Murphy CFO
Wynne Jackson Inc General Contractors-Nonresidential Buildings,...
600 N Pearl St Ste 650, Dallas, TX 75201
Franklin Murphy Manager
Title Emporium, LLC
5979 NW 151 St, Hialeah, FL 33014
Temperature Monitoring System For An Electric Generator
Franklin T. Emery - Orlando FL William G. Craig - Casselberry FL Franklin J. Murphy - Oviedo FL
Westinghouse Electric Corp. - Pittsburgh PA
A generator having stator windings which are water cooled includes a plurality of sensors each for measuring the temperature of cooling water as it is discharged from respective sections of the stator windings and prior to its collection in a common manifold. The outputs of the sensors are combined to obtain an average reading and during an initialization process, each sensor reading is subtracted from the average to derive a correction factor for that particular sensor, for that particular average. The generator is operated so that other averages are selected for the calculation of other sensor correction factors. When operating on line, the correction factors are utilized to obtain a value for a percent of average coil temperature in accordance with the relationship: ##EQU1## where T is the temperature indication provided by the sensor, AVG is the average of all of the sensor readings, and CF is the appropriate correction factor for that sensor for that average.